So you are building a high performance home, well insulated, very airtight, with a very small heating/cooling system. That is great and the Zehnder ComfoSystem is the perfect match for your house. Energy efficient, quiet, easy and fast to install, easy to clean, hypoallergenic.
But what about the Ontario Building Code [OBC]? How can you use the Zehnder ComfoSystem in Ontario?
The following is a quick summary of what you need to keep in mind when designing or spec'ing a Zehnder ComfoSystem in Ontario.
Zehnder designs to ASHRAE 62.2. The ventilation rates that the OBC stipulates are a bit different than that. The ventilation rates used by Zehnder are:
Exhaust Kitchen: 36cfm
Exhaust Bathroom: 24cfm
Exhaust Half Bathroom ("Powder Room", "Water Closet Room"): 12cfm
Supply: divided up to all the other rooms (most of the time 24cfm per bedroom, other rooms on a need basis).
These rates work very well with passive house and often result in whole house ventilation rates close to 0.3ACH.
The OBC prescribes the following ventilation rates (Table 22.214.171.124):
Supply Master bedroom: 10 L/s (36cfm)
Supply Other bedrooms, living room, dining room, family room, recreation room, other habitable rooms, (laundry room, utility room): 5 L/s (18cfm)
Exhaust Kitchen, bathroom or water closet room: 5L/s (18cfm)
Exhaust Basement: 10L/s (for a single open room, with some other stipulations once you divide the space up)
Exhaust fan capacity for the entire dwelling is also set in Table 126.96.36.199.A, but with a balanced ventilation system such as the Zehnder ComfoSystem, you will generally sit much above the minimum required amounts by the OBC.
Overall, the rates a bit different, but can still be accommodated by a Zehnder ComfoSystem. There is also no talk in the OBC about boost rates.
Interior Intake and Exhaust Locations
Ceiling mounted, or
not more than 30mm from the ceiling
Outdoor Intake and Exhaust Locations
Intake minimum 450mm of the ground or the depth of expected snow accumulation
minimum 900mm away from potential sources of contaminants (gas vents or oil fill pipes)
Exhaust minimum 100mm of the ground (which we will never recommend)
Duct types and sizing are also covered by the OBC, but have to be looked at on a project to project basis. The code is very prescriptive about duct sizing, but is not really dealing with systems such as the Zehnder, which use multiple duct runs to single outlets. I would recommend talking to the inspector in charge and explaining how the system comes together.
To apply for your building permit
In order to apply for your building permit according to Part 9 of the OBC, the HRAI has created a design summary, which comes in very handy.
So now it's your turn. Tell us about your projects, or challenges you have in adapting a whole house ventilation system to your high performance home or passive house.
Email us or comment below.